Marketing Automation Platform
I have to design a Power management system in which I have to communicate 160 nos. of Multi-function Meters (of which 20 parameters each).
So, there are in total 3200 nos. of energy parameters.
Kindly tell me how many nos. of Kalki Sync2000/3000 I will have to use, with MODBUS RTU master and IEC101 slave.
It depends on the response time of meter reading, you can decide how many Meter’s can be multidropped on a RS485 link. Generally suggested number is between 12-16. Based on this you will need 10-15 RS485 Ports. So you will need approx 2 SYNC 3000 or 5-6 SYNC 2000
Please, could anybody provide me with a download link for Kalkitech EasyConnect Software. The CD provided is not working!
Hope you were able to obtain the EasyConnect software.
Click here to cancel reply.
Lost your password?
Username or E-mail: